The carbon monoxide (CO) detection market has continued to experience significant growth the past few years, providing installing security contractors with added revenue opportunities. Namely, this marketplace expansion is being driven by legislation requiring the installation of CO detectors in single- and two-family dwellings, and commercial occupancies such as hotels, child and adult daycare facilities, and university dormitories. Currently, there are 29 states along with many major municipalities that have enacted CO regulations.
As security and fire/life-safety professionals evaluate which CO detector to purchase or install, the key is to look for a product that’s not only listed for the intended use, but also has features that comply with the industry’s most recent product standards.
Installing security contractors will need to become educated on the differences between American National Standards Institute (ANSI) and Underwriters Laboratories (UL) standards ANSI/UL 2034 and ANSI/UL 2075, plus be aware of the new requirements of the third edition of ANSI/UL 2075 that became effective in late 2009.
STANDARDS TO LIVE BY
ANSI/UL 2034, Single and Multiple Station Carbon Monoxide Alarms, is the product standard for self-contained CO alarms. These alarms are not designed to be connected to an alarm control panel. The primary operating power for these devices is derived from a battery, a plug-in that uses a two- or three-prong attachment plug or is wired into the dwelling’s AC power line with secondary power backup.
ANSI/UL 2075, Gas and Vapor Detectors and Sensors, is the product standard for CO detectors that are intended to be system-connected to an alarm control panel. This is typically done via conductors, extending from the detector to the control panel or low-power radio frequency signal.
Even though there are two standards for CO detection devices, both have the same alarm thresholds. ANSI/UL 2075 requires detectors to operate within the sensitivity parameters defined in ANSI/UL 2034. The alarm thresholds, set by CO concentration measured in parts per million (ppm), are: no alarm below 30 ppm until after 30 days; 70 ppm for one to four hours (but not less than one hour); 150 ppm for 10 to 50 minutes; 400 ppm for four to 15 minutes.
Page 1 of 3 pages 1
Fire/Life Safety · Fire/Life Safety 2 ·
CO Detection ·
Fire Life Safety ·
Commenting is not available in this channel entry.